REG-0201 Pressure Regulator is a direct operated spring loaded type regulator. These regulators are suitable for Natural Gas, LPG, Air & similar applications.
Technical Specification :
|Surface Treatment||Power Coating|
|Inlet Connection||21.8 x 14 TPI-LH (F)|
|Outlet Connection||1/2" BSP (F)|
Spring Ranges :
|Inlet Pressure||Outlet Pressure||Spring Colour|
|0-17 Bar||0-300 mm WC/ 12"WC||Grey|
|0-200 mbar / 200 mm WC||Yellow|
|0-1 bar / 15 PSI||Red|
Working Principle : When downstream demand decreases, pressure under the diaphragm increases. This pressure overcomes regulator setting which is set by a spring. This results in movement of pad holding assembly towards seat to minimize gas flow area. If the demand of downstream increases, pressure under the diaphragm decreases, spring force pushes the diaphragm lever assembly downwards which results in movement of pad holding assembly away from the seat to increase the gas flow area.
ADJUSTMENT : To increase the outlet pressure setting of the regulator, the spring adjustment screw (Part No.1 0) must be turned clockwise with the help of 14 mm allen key. This requires removal of cap (Part No. 12). Do not adjust the spring to produce an outlet pressure setting above the limit identified on the information label. After the completion of spring adjustment, replace the cap.
Spare Part Use :
|Spare Part No||Part No||Name of Part||Qty|